Connecticut Light and Power (CL&P) recently completed construction of the Stamford Reliability Cable project, a 1.5-mile, 115-kV underground transmission line between the Glenbrook substation and South End substation in Stamford, Conn.
Construction on the $47 million project began in March, and CL&P energized the facilities in November, according to TransmissionHub.
As part of a working group formed by ISO New England (ISO-NE) to study grid reliability in the southwestern Connecticut area, CL&P conducted analyses of transmission load capability between the Glenbrook substation and the South End substation under contingency events. The utility’s analysis indicated that the existing system was insufficient to serve projected customer demands reliably in the Stamford and Greenwich substations area under such events.
CL&P determined that the existing transmission system in this area could potentially experience voltage collapse with thermal overloads exceeding emergency rating and system voltages at substations falling below acceptable limits. The Stamford Reliability Cable project was the working group’s recommended solution to the indentified transmission needs. According to the working group’s findings, the new line will prevent further insufficiencies in the areas surrounding the Stamford and Greenwich substations for at least 20 years.
The New England Power Pool reliability committee voted to recommend approval of the project to ISO-NE in June 2012, and the Connecticut Siting Council on Sept. 12, 2013, approved CL&P’s application to construct the project.
According to the working group, the project will provide the Stamford and Greenwich substations area with a strong electric supply source arising from its connection at the Glenbrook substation to a system of new 345-kV transmission lines installed in southwestern Connecticut since 2006, including the Bethel to Norwalk transmission line, Long Island Cables, the Middletown to Norwalk transmission line, and Glenbrook Cables.
The route for the Stamford Reliability Cable project runs through downtown Stamford and critical commuter rail and highway corridors. According to CL&P, that area presented construction challenges that the project team met through creative solutions that included:
· Tunneling under the Metro-North Railroad right of way (ROW) to avoid impacts to commuters
· Routing the line around the Stamford Urban Transitway, the city’s roadway improvement project between East Main and Atlantic streets
CL&P also is in the process of building the $218m Interstate Reliability Project to address weaknesses in the east to west and west to east transmission of power across Connecticut, Rhode Island, and Massachusetts. The project includes construction of 37 miles of 345-kV overhead transmission lines in existing CL&P ROW.
In early March, the utility began ROW clearing and access road work in preparation for construction through 11 towns in Connecticut. According to CL&P’s project construction web page, foundation work as well as installation of towers and overhead lines were underway as of Dec. 8. The utility plans to energize the facilities later next year.
The new line will exit Connecticut and connect to new facilities in Burrillville, R.I., and the line will terminate in Millbury, Mass. National Grid USA is responsible for construction of the Rhode Island and Massachusetts portions of the Interstate Reliability Project. According to National Grid’s project construction web page, its construction activities in December include cable work in towns in Rhode Island and Massachusetts as well as foundation drilling in towns along the transmission line route in Rhode Island.
CL&P is a unit of Northeast Utilities, and National Grid is a unit of National Grid plc.